JFZ-7D Industrial Dehumidifier
Technical parameters: Dehumidification volume: 7kg / h (30 ℃ RH80%) Circulating air volume: 2000m3 / h Power supply: ~ 220V / 50Hz Input power: 2.8kw Input current: 12.8A Machine net weight: 100kg Dimensions (depth, width, height): 406 × 598 × 1612mm Operating environment temperature: 5-38 ° C Recommended use area: 150-185㎡ (within 3 meters of height) Technical performance of the dehumidifier: Display mode: LCD LCD humidity display, humidity RH10-90% random display. Humidity control: microcomputer control, humidity 1% free setting and control (computer board with power-off memory function) Defrosting function: microcomputer intelligent control, automatic defrost, suitable for low temperature. Compressor: Hitachi flexible scroll compressor, low noise, reliable operation, high energy efficiency. Power supply: 220V power supply, with phase sequence protection function, AC contactor, thermal protection, sensor fault indication error code and other devices. Refrigeration system: The copper heat exchanger with aluminum foil is adopted. The heat exchanger has a compact structure, good pressure resistance and high heat exchange efficiency. Fan design: The centrifugal fan system is adopted, which is characterized by large air volume, low friction, low noise, and long service life. Drainage method: continuous drainage of hoses. Movement mode: Four casters are installed at the bottom, which can be moved freely (see the table for the appearance). Machine appearance: cabinet shape (forward air before the wind). Industrial dehumidifiers Notes for use: 1. The best temperature range for the dehumidifier is 15 ℃ ～ 38 ℃. 2. The doors and windows should be closed as much as possible when using the dehumidifier to achieve the best dehumidification effect. 3. The dehumidifier should be placed in the center of the room to achieve a uniform dehumidification effect, and there should be no obstructions to the air inlet and outlet. 4. The dehumidifier should be placed flat during use, and should not be tilted or tilted to avoid malfunction or abnormal noise of the machine. 5. Place the dehumidifier in a place where it cannot be placed in a place with corrosive gas and high dust. For corrosive gas, please choose a dehumidifier with anti-corrosion function. In a high dust environment, please clean or replace it frequently. Strainer and clean the dust in both devices at the same time to ensure dehumidification performance. 6. After the dehumidifier is transported, please leave it for 4-6 hours before turning it on. Industrial dehumidifier maintenance methods: 1. When there is adhesion or dust on the surface of the body, you can wash it with soapy water, avoid gasoline, petroleum spirit, solvents, etc., and avoid paint or discoloration. 2. The filter should be cleaned regularly (about once every two weeks) to maintain the dehumidification, dust removal efficiency and life of the machine, while avoiding the breeding of bacteria. 3. The two devices should be cleaned regularly with water, and once every two months according to the dust conditions to ensure dehumidification performance. 4. When the machine is not in use for a long time, please unplug the power cord. After cleaning the machine according to steps 1, 2, and 3, wrap the machine in a packing box and store it in a cool and dry place. Application fields: Industrial dehumidifiers are widely used in valuables warehouses, pharmaceuticals, food, electronics, leather, footwear, furniture, printing products, chemicals, tobacco and many other industries. So that the article avoids major losses caused by moisture and mildew. The product has a large applicable area, especially suitable for large workshops and warehouses. It is more suitable for the drying and dehumidification of cartons, cartons, printed products, wood, medicine villages, preserved fruits, seafood, leather shoes and other items. It can strongly remove the internal moisture of materials, quickly dry, and save energy.